If you want to get parametric about it (an approach that makes more sense to me than these arbitrary fast/slow ratings), your typical fuse has two parameters of importance: The current that will raise it to its melting temperature (Imax) and the energy required to melt it (usually expressed in current and time, I²t). Using the second requires evaluating an integral, but it can be approximated pretty easily.
One of the most common errors I see in circuit protection is when wires are sized according to the load, instead of the protection. You see it all the time, you get a lamp fed by these little tiny wires. If you ask about it, the answer always is "the lamp will never draw that much." True, but if you short the lamp, the wire explodes. Wires should be sized according to the available current, not the expected current. If you want to use smaller wires, the available current should be limited first.
Would it be OK to use a BUSSMANN fuse instead of the Littelfuse in your applications?
On the serious side ...... A GREAT short article to explain the importance of selecting the proper circuit protection device rating. It SHOULD be required archiving for EVERY engineer/designer who has any involvement with circuit protection.
On that note, here's an interesting story from my annals.....
We had built an extensive temperature-control system for a large home appliance manufacturer. They had recently converted a critical component of an appliance from a metal unit to an injection-molded piece. The plant supply was basically 480/ 3-phase Delta service. The heaters are rated at 240. Our equipment was designed for the typical 240 service, BUT we also had available an accessory kit for those installations where the mains were 440-480.
When the unit arrived, it was connected by the plant electricians, and set to go. However, it was NOT energized initially because other equipment was not yet installed. When the day finally arrived to power up, the primary side fuses blew immediately (with MUCH gusto, I was told!) When the plant electrician did some preliminary investigation, he discovered that SOMEONE (in our plant) had supplied a set of SUPER FAST-BLOW, CLASS H style fuses in the main disconnect, instead of the RK5 fuses. Obviously, THIS error was the problem. The electrician called our company to inquire, and we apologized for the error, and sent a couple of sets of correct fuses as a token of our appreciation. Once that error was corrected, the temperature controller worked as advertised for years WITHOUT further problems.
Thanks for the article. Engineers often overlook circuit protection and because it's not as straightforward as it appears. To make matters even more complicated, as you pointed out, there are many products available with similar ratings but very different performance. Fuse selection is also dependent on tests that may be performed for agency approval. I once had to increase the size of a fuse a very small appliance because the MOV in the power supply was pulling a great deal of current during Fast Transient Burst testing. The appliance only needed fractional current, but in order to pass FTB I had to increase the fuse size to an Amp or more.
The 3D printing revolution seems to have a knack for quickly moving technology ahead by way of collaborative effort and even a little friendly competition -- all of course in the name of scientific advancement.
Advantech has launched a new series of motion-control I/O modules to meet the increased demands that come with more distributed industrial systems that require control of a growing number of axes and devices.
A quick look into the merger of two powerhouse 3D printing OEMs and the new leader in rapid prototyping solutions, Stratasys. The industrial revolution is now led by 3D printing and engineers are given the opportunity to fully maximize their design capabilities, reduce their time-to-market and functionally test prototypes cheaper, faster and easier. Bruce Bradshaw, Director of Marketing in North America, will explore the large product offering and variety of materials that will help CAD designers articulate their product design with actual, physical prototypes. This broadcast will dive deep into technical information including application specific stories from real world customers and their experiences with 3D printing. 3D Printing is