Microhydroelectric power is making a comeback in electricity generation for homes, farms, and small businesses. This trend is fueled by factors including favorable regulation, rising energy prices, and advances in automation. And do-it-yourselfers worldwide are diving in.
The only requirement to generate electricity is access to a stream with a two-foot drop in water level and two gallons of flow per minute. A hydroelectric system isn’t overly complicated, isn’t difficult to operate and maintain, has longevity, and is often more cost-effective than any other form of renewable power.
Although we’d never built such a system before, we did so by using low-cost components and free technical support, both supplied by AutomationDirect.
In 1980, my father, Arno Froese, began investigating the potential for generating hydroelectricity on his property. The land is situated near the dam of a 64-acre communal lake, allowing access to the 10-foot height differential between the lake and the tailwater on the other side of the dam.
My dad measured the water flowing over the spillway and determined that an average of 40 cubic feet per second flowed through the pond, making it a marginally feasible hydroelectric project. In 2004, my brother Simon discovered our dad’s research and decided to move forward.
This microhydroelectric power plant generates 20kW of power, controlled by equipment from AutomationDirect.
In March 2004, Simon began excavation. For two years, the project was a challenging and sometimes disappointing excavation site, requiring us to dig 17 feet below lake level for the foundation while groundwater and mud continuously seeped into the hole. By the end of 2006, the underwater portions of the plant had been built, a four-foot aluminum pipe through the back of the dam was in place, and a temporary cofferdam was removed. We then installed a refurbished 50hp Francis turbine. Testing determined that the turbine’s optimal speed would be 150rpm.
The hydroelectric system is powered by water draining from the lake that flows through a turbine, which drives three generators via a belt and pulley system. The generators are three Baldor Electric model L1177T 15hp single-phase induction motors.
Driving an induction motor at higher than normal speed generates electricity. Output from the three motors was tied into the local electric grid via the same transformer that formerly only provided power to the property. The utility’s meter now turns backward when our plant supplies more power than we consume.
Great idea. Getting tied into the grid seems to be an important factor here. Saves the whole problem of storage. The perspiration will probably pay for itself in time, since the foundation is the least likely part of this power plant to fail over time.
This interesting case study spotlights the old rule that most great engineering efforts are 80% perspiration (actually, I think it's 90%) and 20% technical smarts. This project simply wouldn't have happened without all that digging, building, and dirt moving.
Linear guides are one of the most important components required for the design of automated or computer-controlled equipment. Aluminum profile extrusions, used for these guides, can enable designed-in functional features.
Focus on Fundamentals consists of 45-minute on-line classes that cover a host of technologies. You learn without leaving the comfort of your desk. All classes are taught by subject-matter experts and all are archived. So if you can't attend live, attend at your convenience.