A question about 4-20 mA loop-powered devices was recently posted to
the "Automation & Control Engineering" group on LinkedIn. Jim Hausch, the
initial poster, was looking for advice on rules and best practices for powering
these devices. He asked: If there are only one or two loop-powered devices in
the system, I just parallel wire the loop-powered devices and that seems to
work OK. In one case, I used a separate small power supply for the single
loop-powered device. Are there any rules or best practices to follow for this?
clarified that his parallel wiring reference relates to the use of one power
supply to provide 24V dc to multiple sensing devices in parallel, so that each
device will have its own connection to its own PLC input.
Noting that PLC 24V dc
supplies often have a low power budget, Terry Trewern, managing director at
Phoenix Engineering, says that this means these power supplies are not always
usable. He also cautions to beware of the difference between sinking and
"Another issue to take account
of is volt drop," Trewern says. "Long cable runs with shared power supplies can
leave you below the minimum 9V at the instrument."
Antonius van Breugel, an
industrial automation professional in Romania, added that loop-powered devices
can be wired in series as long as the total resistance does not exceed 600O.
Pointing out that there are
minimum voltage drops allowed by various manufacturers, Barret Davis, owner of
The AutoMate Co., offered his experience, saying "if you want to use a fuse in
the circuit, you must use a fuse with silver-coated ends. Otherwise, over time,
you can get more voltage drop than the circuit can allow and cause very quirky
and intermittent operation."
According to Davis, "The best
protection against surge is of course using metal conduit for the entire cable
run, preferably EMT or ridged conduit. Most people think that instrument cables
actually shield every frequency. In reality, they only provide attenuation at
frequencies above 1 megahertz."
Roy Gardner, a consultant with Foxboro, replied: "Generally
in the 4-20 mA process measurement family, almost all of the PLC manufacturers
have an input module that has the loop-powering capability built-in. The best
practice in my opinion would always be to use the integral power supply
capability of the control product itself. Any form of external power supplies
leave open questions related to reliability, robustness and error detection
related to the health of the power supply."
Samsung's Galaxy line of smartphones used to fare quite well in the repairability department, but last year's flagship S5 model took a tumble, scoring a meh-inducing 5/10. Will the newly redesigned S6 lead us back into star-studded territory, or will we sink further into the depths of a repairability black hole?
In 2003, the world contained just over 500 million Internet-connected devices. By 2010, this figure had risen to 12.5 billion connected objects, almost six devices per individual with access to the Internet. Now, as we move into 2015, the number of connected 'things' is expected to reach 25 billion, ultimately edging toward 50 billion by the end of the decade.
NASA engineer Brian Trease studied abroad in Japan as a high school student and used to fold fast-food wrappers into cranes using origami techniques he learned in library books. Inspired by this, he began to imagine that origami could be applied to building spacecraft components, particularly solar panels that could one day send solar power from space to be used on earth.
Biomedical engineering is one of the fastest growing engineering fields; from medical devices and pharmaceuticals to more cutting-edge areas like tissue, genetic, and neural engineering, US biomedical engineers (BMEs) boast salaries nearly double the annual mean wage and have faster than average job growth.
Focus on Fundamentals consists of 45-minute on-line classes that cover a host of technologies. You learn without leaving the comfort of your desk. All classes are taught by subject-matter experts and all are archived. So if you can't attend live, attend at your convenience.