Engineers who specify electrical products for industrial equipment tend to have a good working knowledge of UL ratings. However, one rating that gives many engineers trouble is UL 1604, which certifies electrical components for use in hazardous environments. We routinely field questions about UL 1604 and which products comply with it. Here are the answers to some of those questions.
What Is UL 1604?
This rating applies to most types of electrical equipment, circuits, and components operating in conditions that the National Electrical Code (NEC) defines as hazardous due to the presence of flammable gases, combustible dust, or ignitable fibers. The NEC categorizes these conditions as Class I for gases, Class II for dust, and Class III for fibers or flyings. While referred to in North America as UL 1604, this standard has been supplanted by a global standard known as ANSI/ISA-12.12.01. The requirements are similar.
UL 1604 also addresses whether a flammable material is present as part of normal operating conditions or is present only during abnormal operations. The NEC refers to these two scenarios as Division 1 and Division 2, respectively.
Finally, UL 1604 considers different types of hazardous materials according to their NEC codes. Codes A, B, C, and D segment different gases and vapors according to their ignition temperatures. Codes E, F, and G segment dusts according to ignition temperatures and conductivity.
Putting all the classes, divisions, and codes together, here are UL 1604ís key provisions:
Apply to equipment, circuits, and components designed specifically for use in hazardous locations the NEC classifies as Class I and II, Division 2, and Class III, Divisions 1 and 2.
Provide minimum requirements for the design, construction, and marking of electrical equipment for use in these locations.
Cover Class I, Division 2 equipment in which the circuits and components are incapable of causing ignition of a specified gas under normal operating conditions.
Cover equipment constricted to reduce or exclude the entrance of dust in Class II and Class III locations.
Apply under specific atmospheric conditions, including ambient temperature between 5C and 40C, oxygen concentration no greater than 21 percent, and nominal barometric pressure of 1 atmosphere.
Apply to portable battery-powered equipment, other than flashlights, in locations defined as Class I and II, Division 2 and Class III, Divisions 1 and 2.
UL 1604 has other provisions and excludes some electrical equipment covered by other standards. If youíre in doubt about whether a specific component or piece of equipment is compliant, itís a good idea to contact your vendorís application engineering team.
UL 1604 is obsolete and has been superceded by ANSI/ISA 12.12.01. The end of life date for 1604 was July 31, 2012. That being said, this is a good overview of the requirements for either standard. Anyone working with this type of product should also get familiar with the IEC 60079 series standards. They define the hazardous locations (known as explosive atmospheres or ATEX) requirements for europe. IEC60079-0 describes the basic requirements, and the others describe varios protection methods.
More often than not, with the purchase of a sports car comes the sacrifice of any sort of utility. In other words, you can forget about a large trunk, extra seats for the kids, and more importantly driving in snowy (or inclement) weather. But what if there was a vehicle that offered the best of both worlds; great handling and practicality?
As additive manufacturing (including 3D printing) becomes increasingly popular among businesses as a quick and easy solution to creating and evaluating prototypes and end-use products, the debate about whether to outsource production or to purchase equipment for in-house use is at the forefront of industry discussions.
With increasing terrorist threats overseas, organizations are thinking about how best to defend themselves here and abroad. Engineering can play a role, especially when it comes to putting a barrier between yourself and the bad guys.
In the last few years, use of CFD in building design has increased manifolds. Computational
fluid dynamics is effective in analyzing the flow and thermal properties of air within spaces. It can be used in buildings to find the best measures for comfortable temperature at low energy use.
Focus on Fundamentals consists of 45-minute on-line classes that cover a host of technologies. You learn without leaving the comfort of your desk. All classes are taught by subject-matter experts and all are archived. So if you can't attend live, attend at your convenience.